Energy Audit and Accounting for Riksbyggen Fastighetsservice, Gävle
Sammanfattning: Riksbyggen Fastighetsservice is a company whose businesses cope with building construction and related services. The local office of Riksbyggen Fastighetsservice in Gävle has been studied in this project. The local office locates in Näringen 20:4, which was constructed in 1989. The aim of this project is to make a diagnosis of the current situation; find out the most applicable way of optimizing the operation of the facility in order to reduce the energy consumption, to study costs and possible savings and provide assistance with future energy management. Firstly, a study of Energy Balance was conducted. The transmission losses was 57761 KWh; mechanical ventilation losses 3855 KWh; hot tap water heat losses 9579 KWh; natural transmission and infiltration 6897 KWh. On the other hand, heat gain from internal heat was 12707 KWh; solar radiation 8521 KWh; and supply heat 56806 KWh. Secondly, the energy costs have been checked out. 29655 KWh of electricity was consumed in 2008. 5948 KWh was used by 20 fuses electricity and 23707 KWh was for 25 fuses. Lighting, electrical equipment and machine composed the electricity consumption. Lighting consumes 13278 KWh; equipment consumes 6452 KWh; and machine consumes 9925 KWh. Lighting electricity was composed by office lighting and workshop lighting with 4798 KWh and 8480 KWh respectively. Electricity cost is very complicated and flexible in Sweden according to effect and consumption. The total cost of electricity consists of electricity commerce fee and electricity transmission net. Electricity commerce fee includes annual fixed fee, electricity fee, energy certificate and tax. Electricity transmission fee includes annual fixed transmission fee, grid fee and tax. Tax plays vital important role which results in huge total cost. The local office spent 43356 kr on electricity in 2008. 4798 kr was spent on office lighting, and 8480 kr was spent on workshop lighting. On the other hand district heating fee is composed by annual fixed fee, effect fee, energy fee and tax. The local office spent 37142 kr on 56.806 MWh of district heating in 2008. Thus, the local office purchased 86461 KWh of energies and spent 80498 kr in total in 2008. Thirdly, to assist its energy traces and management, three tables were designed. One table is for annual energy consumption and cost in each month with all information of sub-terms on costs. One table is for annual electricity consumption for each electrical equipment and cost in accordance. Another table is for district heating consumption and cost. At last, energy saving possibilities was explored. One way is applying improvements or maintenance of the office construction. The result of Energy Balance shows that transmission losses were 57761 KWh which occupies 74% of the total losses, and it is the biggest bite. As the office was constructed in 1989, if improvements and maintenance can be applied to the insulation of floor, roof and walls, or change the windows, the heat losses can be reduced. However, the other solution might be much more applicable and financial sound. Just go to Clas Ohlson to buy LED 1 W and 3 W lamps to replace the current bulbs. Spending 3009 kr to buy 51 LED incandescent bulbs of 1W effect, and 3576 kr on 24 LED fluorescent of 3W effect, will save 12057 kr every year. The lighting electricity consumption will be reduced from 13278 KWh / year to 264 KWh / year. Instead of spending 16017 kr on lighting, 98% will be reduced, and only 318 kr will be paid. Moreover, the payback is really nice, only 0.42 year. Action! The sooner the better! 20% of energy cost will be saved!
HÄR KAN DU HÄMTA UPPSATSEN I FULLTEXT. (följ länken till nästa sida)